Wacky Weekend: NERC to relax power grid frequency strictures
bicknell at ufp.org
Sat Jun 25 17:12:08 CDT 2011
In a message written on Fri, Jun 24, 2011 at 06:29:14PM -0400, Jay Ashworth wrote:
> I believe the answer to that question is contained here:
> http://yarchive.net/car/rv/generator_synchronization.html 
I wouldn't use a colo that had to sync their generator to the grid.
That is a bad design.
Critical load should be on a battery or flywheel system. When the
utility is bad (including out) the load should be on the battery or
flywheel for 5-15 seconds before the generators start. The generators
need to sync to each other.
Essential load (think lighting, AC units) get dropped completely for
30-60 seconds until the generators are stable, and then that load gets
hooked back in.
I have never seen a generator that syncs to the utility for live, no
break transfer. I'm sure such a thing exists, but that sounds crazy
dangerous to me. Generators sync to each other, not the utility.
Leo Bicknell - bicknell at ufp.org - CCIE 3440
PGP keys at http://www.ufp.org/~bicknell/
-------------- next part --------------
A non-text attachment was scrubbed...
Name: not available
Size: 826 bytes
Desc: not available
More information about the NANOG