Why choose 120 volts?
cmadams at hiwaay.net
Tue May 26 18:51:42 CDT 2009
Once upon a time, Joe Greco <jgreco at ns.sol.net> said:
> And I don't like not having anywhere to plug in my power screwdriver's
> recharger... I suppose I should see if I can find someplace that has
> a transformer of an appropriate size, or does anyone already have the
> part number for something that can provide a few hunderd milliamps of
> 120V from 208? :-)
Isn't 208V usually provided as a connection across two phases of a 3
phase circuit? In that case, you get 120V by going between one phase
and neutral (no transformer required).
You need a NEMA 14 (4 wire) connector to get two phases, neutral, and
ground (provides 1 208V circuit and/or 2 120V circuits) or a NEMA L21
(5 wire) connector to get all three phases, neutral, and ground
(provides 3 208V circuits and/or 3 120V circuits).
Chris Adams <cmadams at hiwaay.net>
Systems and Network Administrator - HiWAAY Internet Services
I don't speak for anybody but myself - that's enough trouble.
More information about the NANOG