Presumed RF Interference
jay at west.net
Sun Mar 5 23:53:08 UTC 2006
Jon R. Kibler wrote:
> Given what I have described, would you think this is an RF interference problem?
No. Many of the devices mentioned are not particularly RF sensitive.
Those that are will recover when removed from the interference source
unless you're talking about levels that are harmful to humans. A
*PATCH PANEL* ??? Short of putting it inside a microwave oven, I can't
think of a means of damaging it with RF, particularly from any distance.
Google "Inverse square law". If you turn the switch off and the
fluorescent lights stay on, then you indeed might want to look into RFI.
> RF problem or not, how would you track down this problem?
I'm 99.9% sure you have a grounding problem. Verify that your power and
equipment grounds have no significant potential difference. Likewise
your telco ground, and the metal building itself. Is the entire
building fed from a single electric meter?
> We are to the point of bringing in a consulting EE, but I am not sure that
> most would be equipped to solve this problem; so, what should we look for
> in a potential consulting engineer?
NEC grounding specification compliance, some who knows the difference
between a groundED and a groundING conductor and is familiar with static
and lightning protection issues.
Jay Hennigan - CCIE #7880 - Network Administration - jay at west.net
NetLojix Communications, Inc. - http://www.netlojix.com/
WestNet: Connecting you to the planet. 805 884-6323
More information about the NANOG