Want to move to all 208V for server racks
toasty at dragondata.com
Thu Dec 2 12:13:09 CST 2010
On Dec 2, 2010, at 12:08 PM, Ingo Flaschberger wrote:
>> For standard 110V service, you use a single-wide breaker and send one hot phase + neutral and you get 110V. The difference between two phases is 208 volts though, so you use a double wide breaker and can send to device without using a neutral wire. Just 2 hots and a ground. If that's all you're doing (you don't need legacy 110V service anywhere) you skip the ground wire going into the panel entirely.
> that one looks dangerous.
Err, I meant "skip the neutral wire". It's still grounded. And there are normally significantly more covers over the panel than this, there were a dozen screws I had to remove to expose all of this. :)
This is a much smaller scale panel though, not far up from a typical home system. The more current you start talking about, the more isolated everything becomes until you wouldn't even be able to see the bus bars like in this one.
More information about the NANOG